Altronix ACM4CB 4 Output Access Power Controller Module w/PTC Protected Outputs
|Part Number: ACM4CB|
4 Output Access Power Controller Module w/PTC Protected Outputs
ACM4CB converts one (1) 12 to 24 volt AC or DC input into four (4)independently controlled Class 2 Rated Power Limited PTC protectedoutputs. Outputs are activated by an open collector sink or normallyopen (NO) dry trigger input from an Access Control System, Card Reader,Keypad, Push Button, PIR, etc. The unit will route power to a varietyof access control hardware devices including Mag Locks, ElectricStrikes, Magnetic Door Holders, etc. Outputs will operate in bothFail-Safe and/or Fail-Secure modes. Unit is designed to be powered byone common power source which will provide power for both the boardoperation and locking devices, or two (2) totally independent powersources, one (1) providing power for board operation and the other forlock / accessory power. The FACP Interface enables Emergency Egress,Alarm Monitoring, or may be used to trigger other auxiliary devices.The fire alarm disconnect feature is individually selectable for any orall of the four (4) outputs.
12 to 24 volt AC or DC operation (setting not required).
Power Supply Input Options:
- One (1) common power input (board and lock power).
- Two (2) isolated power inputs (one (1) for board power and
one (1) for lock/hardware power).
Four (4) Access Control System outputs.
- Class 2 Rated power limited outputs.
- Four (4) PTC protected Fail-Safe and/or Fail-Secure 12VDC power outputs.
- Four (4) PTC protected 12VDC auxiliary power outputs (unswitched).
Red LEDs indicate outputs are triggered (relays energized).
Four (4) Access Control System trigger inputs.
- Four (4) normally open (NO) inputs.
- Four (4) open collector inputs.
- Any combination of the above.
Fire Alarm Disconnect:
- Fire Alarm Disconnect (latching or non-latching) is individually selectable
for any or all of the four (4) outputs.
- Normally open (NO) or normally closed (NC) dry contact input.
- Polarity reversal input FACP signaling circuit.
Fire Alarm trigger LED indicates that the Fire Alarm Disconnect has been activated.
Fire Alarm output relay for triggering auxiliary reporting devices (form "C" contact rated @ 1 amp 28VDC).
Dimensions (approximate): 3.625W x 5.125L x 1.25H